Product Thermal Capacity: 1 - 20 t/h
Working Pressure: 0.7 - 2 Mpa
Available Fuel: Nature gas, coke oven gas, biogas, methanol, liquid propane gas, diesel, heavy oil, light oil, crude oil, etc.
Available Industries: Heat supplying, chemical, food, textile, printing and dyeing, cigarettes and tobacco, fodder, pharmacy, building materials, brewery, rubber, hospital etc.
WNS series horizontal internal combustion boiler is a boiler shell type 3 passes wetback oil/gas fired boiler. After fuel is being atomized by burner, flame is full of the wave furnace and transfer heat via furnace wall, this is 1st pass; the high temperature smoke is collected in reversal chamber and then enters 2nd pass which is grooved tubes bundle area; after heat convection, air temperature gradually falls and goes to front smoke box and turn to 3rd pass, which is smooth tubes bundle area, and then enters chimney passing back smoke box and exhausted to the atmosphere.
1. Digitized manufacture
The key part such as material cutting, rolling, drilling are proceeded by advanced CNC machining process to reduce the assemble stress and extend boiler working lifetime.
The front and back smoke chamber plates are cut by CNC plasma cutting machine and looks tidy and beautiful.
2.Easy operation and maintenance
Fully automatically operating, with automatically adjustment and protection of burning, water level, temperature and steam pressure.
3. Longer working life
Smoke tube and tube sheet connection is expanded first to eliminate the gap between them, then adopt automatic argon arc welding to relief the stress and expand boilers working life.
Longitudinal and girth joint adopt advanced automatic submerged-arc welding for good welding quality. All longitudinal and girth joint will have 100% radiographic inspection.
Fin tube us ND steel or stainless-steel material which avoid low temperature corrosion.
Inspection procedure point is set up to guarantee the sequence of expanding and welding, avoid cracking of the tube sheet holes.
4. Less fuel consumption
High quality aluminum silicate fiber is used with fire clay insulation, to control the boiler body temperature below 45℃ to control heat lost.
Sufficient steam storage room and heating area makes boiler to generate high quality steam and high thermal power.
Condenser is added to reuse the waste heat of the exhausted smoke to increase feeding water’s temperature and reduce emission temperature, which can increase the thermal efficiency above 98% and save operating cost.
This involves the gas consumption of 25 tons gas boiler, the rated evaporation capacity of the boiler is 25 tons per hour, the thermal efficiency is about 93.2%, the calorific value of natural gas is 35.438MJ/nm3, the radiation heating area is 30.2m2, the convection heating area is 187.4 square meters, economizer heating area is 126.86 square
Fire tube or "fire in tube" boilers; contain long steel tubes through which the hot gasses from a furnace pass and around which the water to be converted to steam circulates. (Refer Figure 2.2). Fire tube boilers, typically have a lower initial cost, are more fuel efficient and easier to operate, but they are limited generally to capacities of 25 tons/hr and pressures of 17.5 kg/cm 2.
Author: Heattrade Boiler Ratings and Boiler Load . The oldest method of rating boilers, still used to rate small boilers, is by horsepower (hp). One horsepower is defined as the ability to evaporate 34.5 lbs of water into steam at 212 deg. F and above. Large boiler capacity is generally given in lbs of steam evaporated per hour, under specified steam conditions.
A boilers capacity is usually expressed as kBtu/hour (1000 Btu/hour) and can be calculated as. W = (h g - h f) m (1) where . W = boiler capacity (Btu/h, kW) h g = enthalpy steam (Btu/lb, kJ/kg) h f = enthalpy condensate (Btu/lb, kJ/kg) m = steam evaporated (lb/h, kg/s) Boiler Horsepower - BHP. The Boiler Horsepower (BHP) is. the amount of
Boilers are aimed to produce steam (saturated or super saturated) for commercial or industrial uses. Since capacities for industrial uses are higher compared to commercial ones, so they are often indicated with bigger unit i.e. tons/hr. of steam f
Sep 18, 2008· 2.) rated boiler horsepower (BHP- One bhp is the evaporation of 34.5 pounds (= 15.648 kg) of water per hour from a temperature of 212oF (=100oC) into dry saturated steam at the same temperature. Equivalent to 33,472 BTU/h (= 35.291 MJ/h).) 3.) % of rating. 4.) maximum steam generating capacity in pounds of tonnes per hours.This term is the most
Boiler Cheat Sheet Boiler capacity, Bhp (or hp) vs real capacity in lb / hr. The boiler horsepower (Bhp or hp) is a unit of measurement of the boiler output. Although it is an old unit, it is still very widely used. However, it is sometimes misused and therefore deserves the following clarifications:
Other Useful Information: 1 SQ.FT. E.D.R. = 240 BTUH @215 ° F. 1 Boiler H.P. = 33493 BTU/Hr Where SpGr = Specific Gravity (Water is 1.0). Condensate Pump Sizing: . A: Pump Capacity = 2 x Actual GPM Condensate B: Minimum Receiver Size in Gallons = 1 minute x GPM found in part A C: Pump Head (In Feet) = Static Lift in Feet + Friction Losses in Feet + Pressure In Vessel That’s Being
Answer / manoj kumar. It is common to express the output of steam boilers in Boiler Horsepower, MBTU or in Pounds of Steam delivered per hour. W = (hg - hf) m
No. 76, Xin Da Road, Zhou tie Town, Yixing, Wuxi, China
0086-510-68530066, +86-13506151292Get Latest Price
Copyright © 2020.Zhongzheng Boiler Co., ltd. All rights reserved.