Product Thermal Capacity: 1 - 20 t/h
Working Pressure: 0.7 - 2 Mpa
Available Fuel: Nature gas, coke oven gas, biogas, methanol, liquid propane gas, diesel, heavy oil, light oil, crude oil, etc.
Available Industries: Heat supplying, chemical, food, textile, printing and dyeing, cigarettes and tobacco, fodder, pharmacy, building materials, brewery, rubber, hospital etc.
WNS series horizontal internal combustion boiler is a boiler shell type 3 passes wetback oil/gas fired boiler. After fuel is being atomized by burner, flame is full of the wave furnace and transfer heat via furnace wall, this is 1st pass; the high temperature smoke is collected in reversal chamber and then enters 2nd pass which is grooved tubes bundle area; after heat convection, air temperature gradually falls and goes to front smoke box and turn to 3rd pass, which is smooth tubes bundle area, and then enters chimney passing back smoke box and exhausted to the atmosphere.
1. Digitized manufacture
The key part such as material cutting, rolling, drilling are proceeded by advanced CNC machining process to reduce the assemble stress and extend boiler working lifetime.
The front and back smoke chamber plates are cut by CNC plasma cutting machine and looks tidy and beautiful.
2.Easy operation and maintenance
Fully automatically operating, with automatically adjustment and protection of burning, water level, temperature and steam pressure.
3. Longer working life
Smoke tube and tube sheet connection is expanded first to eliminate the gap between them, then adopt automatic argon arc welding to relief the stress and expand boilers working life.
Longitudinal and girth joint adopt advanced automatic submerged-arc welding for good welding quality. All longitudinal and girth joint will have 100% radiographic inspection.
Fin tube us ND steel or stainless-steel material which avoid low temperature corrosion.
Inspection procedure point is set up to guarantee the sequence of expanding and welding, avoid cracking of the tube sheet holes.
4. Less fuel consumption
High quality aluminum silicate fiber is used with fire clay insulation, to control the boiler body temperature below 45℃ to control heat lost.
Sufficient steam storage room and heating area makes boiler to generate high quality steam and high thermal power.
Condenser is added to reuse the waste heat of the exhausted smoke to increase feeding water’s temperature and reduce emission temperature, which can increase the thermal efficiency above 98% and save operating cost.
Approved Steam Trap Manufacturers. This page lists the Approved Steam Trap Manufacturers (vendors), also provides inspection and test advice to the Steam Trap purchasers buying from vendors, suppliers and distributors.. These vendors have not been evaluated directly by this website, only the manufacturers have been listed here, which they have already assessed and listed in several approved
Author: wareboilers The function of steam trap: Steam traps are installed in steam lines to drain condensate from the lines without allowing the escape of steam.There are many designs of steam traps for high and low-pressure use. types of steam trap types. Steam Trap working. In general, a steam trap consists of a valve and a device or arrangement that causes the valve to open and close as necessary to drain the
The universal mount provides the ability to connect the steam trap to the application with two bolts, thus dramatically reduc-ing the time for installation of a steam trap. 8. Install a strainer as part of the installation of a steam trap. The strainer can be accomplished by the following: a. External strainer ahead of the steam trap b. Steam
Dec 01, 2011· According to the Dept. of Energy approximately 20% of the steam leaving a central boiler plant is lost via leaking traps in typical space heating systems that do not have a steam trap monitoring system. In another article the Dept. of Energy goes on to say that in steam systems that have not been maintained for 3 to 5 years between 15% and 30%
ANSI defines steam traps the following way: . steam trap - Self contained valve which automatically drains the condensate from a steam containing enclosure while remaining tight to live steam, or if necessary, allowing steam to flow at a controlled or adjusted rate. Most steam traps will also pass non-condensable gases while remaining tight to live steam.
Jan 21, 2018· Steam trap, sesuai dengan namanya adalah sebuah alat yang digunakan untuk menjebak steam agar tidak lolos. Steam trap dalam kondisi terbuka ketika hanya condensate saja yang mengalir keluar dari steam trap tersebut.
When installing a steam trap on a steam main, TLV typically recommends the use of traps that discharge condensate continuously, such as the Free Float® type. Other trap types such as disc, bucket, or balanced pressure thermostatic can be used provided that the collecting leg is adequately sized to prevent back-up into the steam main.
2. Steam Drum Steam drum berfungsi sebagai tempat penampungan air panas serta tempat terbentuknya uap. Drum ini menampung uap jenuh (saturated steam) beserta air dengan perbandingan antara 50% air dan 50% uap. untuk menghindari agar air tidak terbawa oleh uap, maka dipasangi sekat-sekat, air yang memiliki suhu rendah akan turun ke bawah dan air yang bersuhu tinggi akan naik ke …
A steam trap is a device that removes condensate from a steam system. A typical steam system will have many steam traps – they are placed at 50-150’ intervals in straight pipe, after every heat exchanger (where the work gets done), and at every location where there is a change of elevation or pressure.
Click to view5:06Feb 20, 2017· Watch as Jude explains a bit of the process that is a steam study Key Words: Steam Boiler Efficency Steam Traps Steam Trap Testing with Infrared - Boiling Point - Duration: 4:00.
No. 76, Xin Da Road, Zhou tie Town, Yixing, Wuxi, China
0086-510-68530066, +86-13506151292Get Latest Price
Copyright © 2020.Zhongzheng Boiler Co., ltd. All rights reserved.